tank pressure should be about 15 lbs and the membrane could be fouled. There is a couple things that could be done here. If you didconect the reject line and put a regular line in its place you can flush the membrane out by running it into a bucet for about 5 minutes, give it a couple litle taps from a wrench or wsomething of that sort. If the bladder in the tank ruppured the tank would weight quite a bit, see if thats the case
The system is 2 years old. The HO changed the all 3 filters and blew (with his mouth) into the control valve. I heard this can cause the valve to not work because of the bacteria that grows in the tiny holes. The tank is heavy, but I am not sure how heavy it SHOULD be.
A forum community dedicated to professional plumbers. Come join the discussion about the industry, safety, finishing, tools, machinery, projects, styles, scales, reviews, accessories, classifieds, and more!