What was all that schedule 80 talk?
My main supplier does not carry a 1" hub x 3/4" MIP adapter in sch.80
I'm also redoing a pressure vacuum breaker loop in sch.40. HO was hassling me about price so I gave him 2 options. sch40 and 80. He went with sch.40. I told him it should really be sch.80 because it's in such a vulnerable position. I also explained that the lawn guys love running into VB loops. He wants the cheap rout, so be it then.