I doubt that one came from Home Depot, it’s the professional series.And a home depot water heater.................
Yeah it’s not worth the $60 extra difference for them to deliver a water heater. I’m not rich yet, I’m still installing water heaters for a living. Can’t forget that.that's usually the case but, to have it dropped off, sitting in the driveway of the home it's getting installed in is worth that extra premium from the supply houses to me.
I was talking about a bracket for the expansion tank. None requiredI am curious about the foil tape on the single wall vent pipe. Is that a requirement in your jurisdiction? I have never seen that as a requirement. The vent for a Catagory 1 appliance is under negative pressure. The IFGC has very little information on installation requirements of single wall "vent" pipe. Very little on specifics as to how sections of single wall vent pipe are to be fastened together, sealed, supported. I am an oldtimer, and we always used at least 3 screws in each joint of single wall vent pipe. Never used tape. Anybody have jurisdiction requirements that go farther than screws in each joint? Such as how often the vent must be supported horizontally? For instance IFGC Chapter 5 vents says All portions of single wall metal pipe shall be supported for the design and weight of the material supported. That leaves a lot up to the discretion of the AHJ.
Can you tell me what code numbers that’s in the model codes under ?Most if not all codes forbid a valve that can isolate a safety device from the system it's protecting.
What code would that be ?In My Opinion, this code requires a valve at the expansion tank. See 7.
606.1 Location of Full-Open Valves
Full-open valves shall be installed in the following locations:
- On the building water service pipe from the public water supply near the curb.
- On the water distribution supply pipe at the entrance into the structure.
- On the discharge side of every water meter.
- On the base of every water riser pipe in occupancies other than multiple-family residential occupancies that are two stories or less in height and in one- and two-family residential occupancies.
- On the top of every water down-feed pipe in occupancies other than one- and two-family residential occupancies.
- On the entrance to every water supply pipe to a dwelling unit, except where supplying a single fixture equipped with individual stops.
- On the water supply pipe to a gravity or pressurized water tank.
- On the water supply pipe to every water heater.